- CE Marked.
- Compact Duct Sleeve up to 120 minute rating to EN 1366-3 : 2009.
- Uncapped / Uncapped (Open | Open) fire tested as required for ventilation systems.
- Suitable for use through a wide range of fire partition walls.
- Reduced profile - 10-15mm thickness - allows installation at any position in the wall, even tight to the floor slab, without removing the top side.
- Does not need metal sleeving.
- Sleeve can be easily fitted and only requires access from one side.
- Sleeve can be slit to allow retrofitting.
- Astroflame do not use "desk top studies" to approve products, instead we use an extensive range of "Primary test evidence" and formal assessments from approved test bodies.
The Astro Low Profile Duct Sleeve are a family of CE Marked fire penetration seals designed to firestop PVC ventilation ducts/pipes when installed through fire rated constructions.
The unique vacuum formed intumescent material design ensures that the expansion direction of the material crushes and seals the ducting in a fire situation without the need for any additional metal sleeving.
The lack of metal sleeving, not only makes installation easy, it also limits the risk of heat transfer through the structure as well as allowing compression to ensure a tight seal against fire and smoke or tight fitting against the ceiling soffit where needed.
The Astro Low Profile Duct Sleeve provide fire resistance ratings for Integrity (E) and Insulation (I) for up to EI120 minutes depending on the construction.
Fire Tested for both internal and external wall constructions. The Fire Sleeves are CE Marked with a European Technical Assessment.
The duct sleeves are available to fit common sizes of rectangular and circular plastic ventilation ducts.
- Size: Internal Width: N/A, Internal Height: 127mm Diameter, Length: 280mm
- Colour: Red
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email firstname.lastname@example.org
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
Please refer to the ETA sheet for fields of application for this product. For further information on installation requirements please refer to the duct manufacturer data and wall specification to ensure the compatibility of this product, if in doubt please contact the technical team with services and wall specification on Tel: +(0)1329 841416 or email email@example.com
Download and review any of the following information:
Certification/Fire Test Reports:
CE Marked Documents
'DoP's are 'Declaration of Performance'
'CoC's are 'Certificate of Constancy of Performance'
'TDS' 'Technical Data Sheets'
'ETA' European Technical Assessment Sheet