- CE Marked.
- 4-in-1 Solution Fire, Acoustic, Thermal and Vapour Seal.
- Up to EI120 Minutes Fire Rating in Gypsum Walls and Solid Floors.
- Up to EI240 Minutes Fire Rated in Solid Walls.
- Suitable for both Metal and Plastic Pipes.
- Simple & quick to install, no fixings or sleeving required.
- Available to suit pipe diameters of 15mm to 169mm.
- 1 length of Fire Sleeve can replace two fire collars.
- Lubrizol Approved.
- Cost effective, can be cut to length.
The Insulated Thermal Fire Rated Pipe Sleeve are a range of passive fire protection penetration seals designed to firestop insulated metal and combustible plastic pipes.
The Fire Sleeves offer Fire, Acoustic, Thermal and Vapour seal performance to a range of pipes passing through various wall or floor constructions.
The CE Marked range are fire tested in accordance with EN 1366-3 with additional testing and assessments to BS 476 Part 20.
The Insulated Thermal Fire Rated Pipe Sleeve are manufactured from a unique, low smoke, zero halogen intumescent material. The Fire Sleeves are supplied pre-formed and ready to install to suit a variety of pipe diameters.
With a nominal thickness of 25mm, the compressible intumescent sleeve is supplied wrapped in a reinforced aluminium foil allowing it to be cut down its length and retro-fitted around the pipes. This provides an effective fire, smoke and acoustic seal whilst also allowing for some thermal movement. Fire Ratings of EI30, EI60, EI90, EI120 or even up to EI240 minutes are offered depending on the construction type.
- Length 300mm. Wall thickness 25mm.
- Internal diameter size 159mm.
We have technical representatives who provide assistance in the selection and specification of the products on this site and should be consulted for exact installation and product suitability. Ensure an early engagement with ourselves, designers, main contractor and specialist installers before any installation. Other trades and/or manufacturers may need to be consulted. For in-depth information, specification and technical advice please call our Head Office on Tel: +(0)1329 841416 or email firstname.lastname@example.org
All interested parties, designer, specifier, main contractor and specialist installers should provide access to allow the fire stopping seals to be regularly inspected and maintained, as well as records kept of such maintenance at minimum periods of 12 months, as required by the Regulatory Reform Order, and repaired if necessary. Reference should be made to ASFP TGD 17 Code of Practice for the Installation and Inspection of Fire Stopping.
It is vital that those entrusted to design or install a fire stopping product have the necessary levels of competence to undertake the task professionally and thoroughly. The level of competency required will be commensurate with the expected complexity of the building. All designers must eliminate, reduce or control foreseeable risks that may arise during installation, construction or maintenance when preparing or modifying designs. Clients should ensure that the principal designer and principal contractor carry out their duties under CDM regulations. The ASFP foundation course in passive fire protection provides essential knowledge as part of demonstrating competency and understanding in this key fire protection specialism.
Please refer to the ETA sheet for fields of application for this product. For further information on installation requirements please refer to the pipe manufacturer data and wall specification to ensure the compatibility of this product, if in doubt please contact the technical team with services and wall specification on Tel: +(0)1329 841416 or email email@example.com
Download and review any of the following information:
Certification/Fire Test Reports:
CE Marked Documents
'DoP's are 'Declaration of Performance'
'CoC's are 'Certificate of Constancy of Performance'
'TDS' 'Technical Data Sheets'
'ETA' 'European Technical Assessment Sheet'